Anguilla, Mississippi Fume and Dust Extraction Arm Systems
Anguilla Industrial exhaust systems are designed to capture smoke, fume, dust, high-temperature air, and corrosive gases. These "pollutants" are ducted to an air cleaner (purification system) before discharge to the outside or returned to the workspace. Capturing air-entrained materials is best accomplished at the emission source, defined as source capture.
Multiple arm designs are available depending on the airstream constituents. The parameters evaluated are temperature, explosivity, corrosiveness, and particulate, all factors determining the type of arm that should be selected for a process application. Matching your expected exhaust volume and arm useage with the required exhaust CFM, pressure loses, and airstream being captured is what we do. SysTech has successfully applied extraction arms for over thirty years and will assist with the correct selection for your process.
Anguilla, Mississippi Fume extraction arms with hoods or suction nozzles are the number one tool to maximize source capture efficiency. They capture the contaminated airstreams while getting close to the source without disrupting or slowing down the work process or collecting too much useable product. When the task or workpiece is difficult to access, in an isolated area, or along awkward points on an assembly line, extraction arms are a proven solution for maximum particulate, smoke, and fume collection.
Anguilla, Mississippi Stainless Steel Extraction Arms
Aggressive airstream chemistry may require the arms to be constructed of 304 stainless steel. The tubing and hood are stainless, with external adjustment joints at the hood and swivel joints. Arm assemblies have a wall mounting bracket and an internal damper for airflow adjustment and shutoff. The standard flex hose at the joints is an FDA Pur Antistatic hose. Stainless steel arm tube diameters vary from three to eight inches, and arm lengths from three feet up to fourteen feet, all suitable for washdown applications. 316 stainless steel construction is an available option.
- Available in hanging and benchtop models.
- Clear anti-static FDA hose rated for 200 degrees Fahrenheit.
- 304 SS grab handle on the hood for easy mobility and positioning.
- Optional fume exhaust fans in aluminum, carbon steel, or PVC.
- Arm diameters include 3", 4", 5", 6", and 8", and arm lengths include 3', 5', 7', 8', 10', and 14'.
- External joints are anodized aluminum.
- Tubes, hood, internal shutoff damper, and duct connection collar are all constructed of 304SS
New and Retrofitted Extraction Arm Systems in Anguilla
When you install a new fume extraction arm or arms, it improves air cleaning system performance, resulting in a cleaner work environment. Expectations can be met if all-important selection factors are considered and limitations for capture are pointed out.
If you are repairing, replacing, or adding a new arm or arms, to an existing system, the critical components of the fume exhaust system should be reviewed, including the duct system, the exhaust fan (s), and the air cleaning device. Systems are only as efficient as their individual parts, and SysTech will review your components with you to evaluate if your system is operating at peak performance.
Anguilla, Mississippi Weld Fume Extraction Arm
The demand for weld smoke extraction arms is always high and mandates an arm category. Depending on the application, different designs use either smooth wall or flex hose tubing. Both designs use external positioning joints and a hood with an internal adjustable damper. The units are typically wall-mounted but have ceiling and floor support bracket options. Arm diameter options range from six to eight inches, and arm lengths vary from three feet up to thirty-six feet. Personal weld fume packages include a single extraction arm, exhaust fan, and air filter.
- Arm diameters include 3", 4", 5", 6", and 8", and arm lengths include 3', 5', 7', 8', 10', 14', 16', 23', 30', and 36'.
- Standard units include a wall bracket. Ceiling mount options are available.
- Low-pressure drop
- Optional fume exhaust fans in aluminum, carbon steel, or PVC.
- Shut off dampers built internally.
Exhaust Fans for Fume Extraction Arms in Anguilla
Industrial exhaust system arms often need a connection to an exhaust fan for isolated applications or when needed for additional static resistance when connecting to an existing duct system. Fan CFM and static pressure must be examined in both cases to maintain system performance. When coupling with an exhaust fan, it should be constructed of similar or compatible materials to the extraction arm.
Cast Aluminum Pressure Blowers
Cast aluminum pressure blowers are typically supplied by manufacturers where there is a non-corrosive airstream. They are light, come in a wide range of designs, are compact, and are AMCA B spark-resistant as standard. Motors are available in single and three-phase TEFC and EXP frames.
Carbon Steel Fume Exhauster
If conditions of the airstream are suitable, a carbon steel painted fan is selected in a direct drive arrangement with a horizontal mount configuration that requires minimal space. Steel blowers have the option for AMCA construction up to AMCA A and 304 and 316 SS construction. Motors are available in single and three-phase TEFC and EXP frames.
Industrial Plastic Fume Exhaust Fans
Corrosive environments require materials of construction that will not degrade over time. Plastic construction is misunderstood as fragile, but industrial-grade designs are compatible with the harshest environment. The plastics typically used for construction are PVC or polypropylene (P.P.) and are an excellent choice for the efficient conveyance of corrosive, chemically laden, humid, or polluted gases, fumes, and air. Motors are available in single and three-phase TEFC and EXP frames.
Anguilla, Mississippi Extraction Arm Selection and Performance
The first step in extraction arm selection is determining how the arm will be used, the required work area, and any space constraints for hood positioning. The required arm length is determined by the arm mounting location and where the capture hood will be used. The selection of an extraction arm is based on several criteria:
Performance – The volume of exhaust air required is in cubic feet per minute or CFM, and the resistance to airflow is in inches W.G. or static pressure (S.P.) Because the arms are moveable, the S.P. thru the arm will change with arm and hood positioning.
The total S.P. requirement for an extraction arm is based on arm length, the number of arm elbows, the type of arm tubing, the type of hood, and internal or external support structure. Arm manufacturers include this value in their literature along with performance curves. The static pressure will change when the arm is repositioned (extended or compressed). Depending on the arm selected and the work area size, it could be a minor or significant change in fume capture. When choosing an arm, it is best to size the S.P. requirement as the worst case.
The CFM requirement for source capture varies with the collected fume, dust, or product. The amount of collected air is based on the hood capture efficiency, the position of the hood to the fume source, and any crossflow air currents. Follow the project design specifications or contact SysTech for recommended CFM.
Mounting Location - Where the arm is located will determine the arrangement of the design. We can provide them in bench, wall, or ceiling mount designs. These should be selected to access the captured waste stream by locating the arm as close as possible to the process.
Environment – Dirt or abrasive materials in the ambient room air may adversely affect the arm joints. Also considered is hood capture efficiency being compromised where crossflow air currents exist in the workspace.
Airstream constituents – What is in the airstream will determine the materials of construction, most notably, explosion or fire hazards, abrasive materials, and aggressive chemicals. Materials can be aluminum, polypropylene, stainless steel, and in some cases, carbon steel.
Applicable Codes – Typical requests include FDA compliance with food-grade materials or minimizing fire/explosion potential.
Frequency of use – Infrequent usage or continual use dictates light or heavy-duty construction.