Allentown, New Jersey Fume and Dust Extraction Arm Systems
Allentown Industrial exhaust systems are designed to capture smoke, fume, dust, high-temperature air, and corrosive gases. These "pollutants" are ducted to an air cleaner (purification system) before discharge to the outside or returned to the workspace. Capturing air-entrained materials is best accomplished at the emission source, defined as source capture.
Multiple arm designs are available depending on the airstream constituents. The parameters evaluated are temperature, explosivity, corrosiveness, and particulate, all factors determining the type of arm that should be selected for a process application. Matching your expected exhaust volume and arm useage with the required exhaust CFM, pressure loses, and airstream being captured is what we do. SysTech has successfully applied extraction arms for over thirty years and will assist with the correct selection for your process.
Allentown, New Jersey Fume extraction arms with hoods or suction nozzles are the number one tool to maximize source capture efficiency. They capture the contaminated airstreams while getting close to the source without disrupting or slowing down the work process or collecting too much useable product. When the task or workpiece is difficult to access, in an isolated area, or along awkward points on an assembly line, extraction arms are a proven solution for maximum particulate, smoke, and fume collection.
New and Retrofitted Extraction Arm Systems in Allentown
When you install a new fume extraction arm or arms, it improves air cleaning system performance, resulting in a cleaner work environment. Expectations can be met if all-important selection factors are considered and limitations for capture are pointed out.
If you are repairing, replacing, or adding a new arm or arms, to an existing system, the critical components of the fume exhaust system should be reviewed, including the duct system, the exhaust fan (s), and the air cleaning device. Systems are only as efficient as their individual parts, and SysTech will review your components with you to evaluate if your system is operating at peak performance.
Allentown, New Jersey Fume Extraction Arm Optional Accessories
Fume extraction arms have optional accessories that include:
Tube materials – For those arms using tubing, construction materials include painted steel, aluminum, stainless steel, P.P., or PVC. Extraction arms that use flex hoses can use clear, fire retardant, high temperature, or anti-static hoses.
Ceiling Mount - For applications where arms are mounted/supported by the ceiling. The ceiling bracket varies in height depending on the height of the hard deck or Unistrut.
Wall Mount - A wall bracket designed to mount the arm to any wall or beam within the facility.
Custom hoods – To maximize fume capture, standard circular or scoop-shaped hoods can be changed to a slotted design, rectangular, flat, or custom fabricated.
Nozzles - To get even closer to source capture, suction nozzles and flexible suction nozzles are available.
Hood lights – Lights can be attached to the arm hood to provide better vision at the work point. Often used in welding applications.
Floor Stanchion - When the ceiling is too high, or there are no walls, a floor stanchion can be used to mount the arm.
"General Purpose" Allentown, New Jersey Industrial Extraction Arm
We label these arms a standard issue because they can be universally applied to most fume and dust extraction applications. The general-purpose arm is suitable for capturing smoke, dust, or any non-corrosive product. They are constructed of smooth powder-coated steel or aluminum tubing, a capture hood with adjustment grips, flex hose joint covers, and external adjustment brackets for the hood and swivel joints. The assemblies come standard with a wall mounting bracket but also have ceiling and floor support brackets available. An internal damper is included for airflow adjustment or shutoff. The arm mounting brackets allow for 180⁰ and 360⁰ rotation. Arm diameter options range from three to ten inches, and arm lengths vary from three to thirty-two feet. The maximum airstream temperature for these arms is about 180 degrees Fahrenheit.
Features and options:
- Arm diameters include 3", 4", 5", 6", and 8", and arm lengths include 3', 5', 7', 8', 10', and 14'.
- Includes duct connection collar
- A shutoff damper is built into the lower tube.
- An optional fume exhaust fan in aluminum, carbon steel, or PVC.
- Grab handle around the hood that is aluminum powder-coated black.
- Black hose rated for 195 degrees Fahrenheit (intermittent 260 degrees Fahrenheit)
- The wall bracket is powder-coated black.
Allentown, New Jersey Fume Extraction Arm Mounting and Supports
Fume extraction arms are continually moved, extended, and rotated, requiring them to be rigidly supported and mounted securely. A few factors affect mounting location: 1) the location of the fume source, 2) the coverage area for where the arm is used 3) the central system duct where the fume arm is connected.
Mounting options include:
Wall Mount - With duct systems running against a wall, mounting the arm (s) with brackets secured to a block wall or column is typical. If the central system duct is along the ceiling, on an outside wall, or mid-wall, there are designed brackets to fix the arm in place.
Bench Mount - Exhaust duct running along the floor allows mounting to a bench or tabletop. This mount has a standard option bracket for attaching the arm. Another standard bench mount is on a portable air filter or dust collector.
Ceiling Mount - Mounting the arms in the ceiling is an option if joists are present. A support weldment could be fabricated if a ceiling mount is a requirement. For low-weight short arms, the installation contractor can fabricate a wood fixture.
Stanchion Mount - When arms are located in the center of a facility having high bay areas, a stanchion will allow the mounting of an arm and hold it rigidly in place.
Allentown, New Jersey Extraction Arm Selection and Performance
The first step in extraction arm selection is determining how the arm will be used, the required work area, and any space constraints for hood positioning. The required arm length is determined by the arm mounting location and where the capture hood will be used. The selection of an extraction arm is based on several criteria:
Performance – The volume of exhaust air required is in cubic feet per minute or CFM, and the resistance to airflow is in inches W.G. or static pressure (S.P.) Because the arms are moveable, the S.P. thru the arm will change with arm and hood positioning.
The total S.P. requirement for an extraction arm is based on arm length, the number of arm elbows, the type of arm tubing, the type of hood, and internal or external support structure. Arm manufacturers include this value in their literature along with performance curves. The static pressure will change when the arm is repositioned (extended or compressed). Depending on the arm selected and the work area size, it could be a minor or significant change in fume capture. When choosing an arm, it is best to size the S.P. requirement as the worst case.
The CFM requirement for source capture varies with the collected fume, dust, or product. The amount of collected air is based on the hood capture efficiency, the position of the hood to the fume source, and any crossflow air currents. Follow the project design specifications or contact SysTech for recommended CFM.
Airstream constituents – What is in the airstream will determine the materials of construction, most notably, explosion or fire hazards, abrasive materials, and aggressive chemicals. Materials can be aluminum, polypropylene, stainless steel, and in some cases, carbon steel.
Environment – Dirt or abrasive materials in the ambient room air may adversely affect the arm joints. Also considered is hood capture efficiency being compromised where crossflow air currents exist in the workspace.
Mounting Location - Where the arm is located will determine the arrangement of the design. We can provide them in bench, wall, or ceiling mount designs. These should be selected to access the captured waste stream by locating the arm as close as possible to the process.
Applicable Codes – Typical requests include FDA compliance with food-grade materials or minimizing fire/explosion potential.
Frequency of use – Infrequent usage or continual use dictates light or heavy-duty construction.